7th Sep 2020
7th Sep 2020
A domestic property in BS 9251:2005 is defined as dwelling that has no more than one family unit. This could be a house, individual flats and maisonettes. BS 9251:2005 requires that a sprinkler system must be designed to ensure that two sprinkler heads can be fed by a water supply for at least 10 minutes. With the introduction of the BS9251:2014 all are regarded as residential properties and fire sprinkler systems are divided into categories 1, 2 and 3. Catagory 1 residential sprinklers are broadly equivalent to what previously domestic fire sprinklers or home fire sprinklers.
A residential property in BS 9251:2005 is classed as a care home, nursing homes, blocks of flats, home of multiple occupancy (HMOs). BS 9251: 2005 requires that a sprinkler system must be designed to ensure that four sprinkler heads can be fed by a water supply for at least 30 minutes.
A residential system is different from a commercial system. It is therefore important to specify the terminology clearly.
Unit 1 Bowlings Corner, Marley Lane, Battle, East Sussex, TN33 0RE
5 Snape Road, Macclesfield, Cheshire, SK10 2NZ
What Triggers Fire Sprinklers and can they go off accidentally? Do fire sprinklers go off if you hit or touch them? How sensitive are fire sprinklers? Do fire sprinklers detect vape? https://t.co/HAKEFWqjqS ☎️01625 467245 ☎️ #Ultrasafe #HereToHelp #ThinkSprinkler #Sprinkler https://t.co/eTTyVv3Lkx
Simply complete our form below and we’ll get in touch very soon to answer your enquiry.